Mixing valve 1 “NPT for domestic hot water
For point of distribution in domestic water systems and radiant hydronic heating systems.
Low-lead brass valve body and fittings.
Internal anti-scale materials.
Peroxide-cured EPDM seals.
Locking set point knob.
Max working pressure: 200 psi
Max recommended differential pressure: 20 psi
Max inlet temp: 200˚F
Adjustable range: 85˚ – 150˚F
Min flow for optimum performance: 1.0 gpm
Compliance with the following codes: IPC, IRC, UPC and NPC for use in accordance with the U.S. and Canadian plumbing codes
Compliance with the following standards:
NSF/ANSI 372 – Drinking Water System Components – Lead Content
Reduction of Lead in Drinking Water Act – California Health and Safety Code 116875
S.3874 – Reduction of Lead in Drinking Water Act
Vermont Act 193 – The Lead in Plumbing Supplies Law
Maryland’s Lead Free Law Hb.372